@NaziGods I just cat watch anymore .. #ohmyeyes @Asschin74
Donde estará el error? #OhMyEyes!
Here's an #ohmyeyes from last week. When clipped properly the chances of cable getting damaged like this are reduced.
#ohmyeyes Sub-standard installs like this are what cause faults on your fire alarm. Beware of people "chucking it in"
#ohmyeyes This is not how a detector should be mounted on a ceiling tile. One yank & the cable will be out the terminals
#ohmyeyes fault finding all day....shoddy install caused earth fault. Found it here. Never join fire cable like this!
#ohmyeyes If you must join fire cable...this is not how to do it! Found an earth fault here. Who signed this alarm off?!
#ohmyeyes fire alarms should have battery back-up. 24v requires 2x12v batteries in series. This won't work!
#ohmyeyes an emergency lights test switch being used to isolate a fire alarm & no zone chart - tut tut *wags finger*
#ohmyeyes Check out this old "Flag" fire alarm system. This is from another age! @MeansofEscape
@MeansofEscape every day's a school day. Ever seen these bi-metalic strip detectors? What year you reckon? #ohmyeyes
@MeansofEscape @SYAMLogBooks @Comtec_Fire check out this novelty "fire alarm" spied in a welsh petrol station #ohmyeyes
#ohmyeyes Manchester based Gent 24 SI company did this. Shocking disregard for standards. Friday PM butchered base job.
Look at this circus act! Extreme window cleaning/texting. #levitation #ohmyeyes #health&safety
Back in 230v fire alarm hell. #ohmyeyes
#ohmyeyes Dear students. This is a heat detector so covering it up is pointless; it won't go off when you light up!
#ohmyeyes If your fire alarm wiring looks anything like this it's probably time for an upgrade. #yorkshireday
#ohmyeyes fault finding on aged 240v alarm; LOOK a very bad person has used copper wire to replace fuse. #firesafety
#ohmyeyes anyone want to hang their washing out on these fire alarm cables? Does your system comply? #ClippedEvery300mm
#ohmyeyes smoke detector should be 300mm from light fittings unlike this one at @Casa__Hotel Barca Bar. DM for a pro.
#ohmyeyes smoke detector in Barca Bar @Casa__Hotel does not comply with regs. Should be 300mm from light fitting #onduty
#ohmyeyes cable spaghetti here and then our neatly clipped regs-compliant fire alarm cable along the wall. #properjob
#ohmyeyes cable spaghetti...& some neatly clipped fire alarm cables (the red ones on wall). Does your fire alarm comply?
©2014 Twitpic Inc, All Rights Reserved